Gladshtein, V. I.
A procedure for estimating the wall thickness margin for operation during a specified design service life under creep conditions if the metal of articles contains initial flaws is presented. The analysis is carried out taking as an example parts of steam lines made of two different grades of steel: a cast elbow with the size d = 426 × 30 mm made of 15Kh1M1FL low-alloy steel and a pipe bend with the size d = 219 × 32 mm made of EI-756 12% chromium steel. The calculated assessments are compared with the results obtained from long-term operation.
Bozovic, L. I.
This document is an English-language abstract (approximately 1,500 words) of a three-part volume on the psychology of child personality development. In part one, the author shows that psychology is one of the most important scientific disciplines on which education is based, particularly because of its contribution to the scientific planning of…
Gladshteyn, V. I.; Troitskiy, A. I.
Research of a metal of the stop valve case (SVC) of the K-300-23.5 LMZ turbine (steel grade 15Kh1M1FL), destroyed after operation for 331000 hours, is performed. It's chemical composition and properties are determined as follows: a short-term mechanical tensile stress at 20°C and at elevated temperature, critical temperature, fragility, critical crack opening at elevated temperature, and long-term strength. Furthermore, nature of the microstructure, packing density of carbide particles and their size, and chemical composition of carbide sediment are estimated. A manifestation of metal properties for the main case components by comparison with a forecast of the respective characteristics made for the operating time of 331000 hours is tested. Property-time relationships are built for the forecast using statistical treatment of the test results for the samples cut out from more than 300 parts. Representativeness of the research results is proved: the statistical treatment of their differences are within the range of ±5%. It has been found that, after 150000 hours of operation, only the tensile strength insignificantly depends on the operating time at 20°C, whereas indicators of strength at elevated temperature significantly reduce, depending on the operating time. A brittle-to-ductile transition temperature (BDTT) raises, a critical notch opening changes in a complicated way, a long-term strength reduces. It has been found empirically that the limit of a long-term strength of the SVC metal at 540°C and the operating time of 105 hours is almost 1.6 times less than the required value in the as-delivered state. It is possible to evaluate a service life of the operating valves with the operating time of more than 330000 hours with respect to the long-term strength of the metal taking into account the actual temperature and stress. Guidelines for the control of similar parts are provided.